The first thing you will need to discover is whether you are dealing with a three-phase motor. You may already know this from the application, but another giveaway is that the lead wires of most three-phase motors are single colors, not multiple colors, and usually identified with numbers. If, on the other hand, the motor diameter is less than seven inches and has a terminal board, it is most likely a single-phase motor.
The shield strongly attenuates the electric field noise. Core to shield capacitance is added to the stray capacitance, increasing ground currents in the loop. These currents generate a magnetic field. It is important to minimize the area of this loop as far as possible by routing the cable close to grounded metalwork.
The PWM Drive (pulse-width modulated drive) to motor power conductors are typically the most intense noise source in a system. Proper implementation of shielding, grounding, splicing, and treatment of excess cable is essential to reducing noise in your system.
Motor cables are defined as long when the motor frame is not bonded close enough to the drive panel to be considered a single ground plane. To be considered a single ground plane, the parts must be connected by a surface which is no longer than ten times its width.